PMMI Lighting does not sell the following items, but they are readily available online and at building supply retail outlets. Following are links to products that we recommend, but certainly ease to search engines allows you to shop around.
The Raspberry Pi, located in the HUB has an HDMI input and USB port that allow the ability to add on a monitor, and keyboard to the system. Because this is not necessary for functionality monitors are not a part of the standard package, but hooking one up to the system makes viewing the system activity, and controlling your system effortless.
Purchase ONLY solid copper Cat5/6 cable.
Copper coated aluminum which is half price will NOT work with our system.
Links are to Cat5/6 stranded patch cables. These are acceptable to use as long as they are SOLID COPPER. The cables in these links already have the RJ45 connector on them, that is specific to patch cables. IF you have to change out the connector, it is NOT the standard RJ45 connector, but is a connector specific to stranded wire.
Stranded cables should NOT be used for any of the Home Runs, but can be used for jumpers between lights and panel cables like short jumpers from panel to AC interface.
- 4 ft. Patch Cable (use red for fixtures, green for switches, yellow for motion detectors)
- 5 ft. Patch Cable (use red for fixtures, green for switches, yellow for motion detectors)
- 6 ft. Patch Cable (use red for fixtures, green for switches, yellow for motion detectors)
- 7 ft. Patch Cable (use red for fixtures, green for switches, yellow for motion detectors)
- Plenum Wire – If your build is in an area that requires Plenum Rated wire, the above wire will not meet those specifications. With plenum wire, solid copper is required.
Links to Cat5/6 are acceptable to use as long as they are SOLID COPPER. These do NOT have the RJ45 connector on them. Bulk cable should be used for ALL cable runs over 7 feet long.
- Bulk Cable, Red, 1000 ft. (use red cable for fixtures)
- Bulk Cable, Green, 1000 ft. (use green cable for switches)
- Bulk Cable, Yellow, 1000 ft. (use yellow cable for motion detectors)
Plenum Wire – If your build is in an area that requires Plenum Rated wire, the above wire will not meet those specifications. With plenum wire, solid copper is required.
Connectors and Tools
Links are to Cat5 connectors and tools. If other size cable is used, make sure appropriate connectors are ordered.
- RJ45 Cat5 Connectors – Male (necessary to use with bulk cable)
- Heavy Duty Crimp Tool ONLY (necessary to attach RJ45 Cat5 connector to bulk cable)
- EZ-RJ45 Termination Kit, with Nylon Zip Case, EZ-RJ45 Crimp Tool Professional Electrician’s Scissors, and Cat 5 Cable Jacket Stripper (tools that are helpful for installation)
- Labels (NECESSARY – you’ll thank us later)
The Lighting & Control Systems by PMMI Lighting, LLC operate on 12, 24, 26, or 48V DC. It can be powered by 120V and 240V AC grid power using an AC-DC power supply, or off-grid using solar or wind.
- Solar Panels, Charge Controllers, Batteries and Mounts
- DC to DC Converter for 12V DC Power for Electronics – See SD-50B-12 and SD-50C-12 for 24V and 48V solar systems, respectively.
- AC to DC Power Supplies – See RS-50-12 to power 12V DC electronics, and LRS, SE, RSP Series power supplies for V2 (LED Drivers)
In the event of a power outage, a UPS (Uninterruptable Power Supply) can prevent the lighting control system from an ungraceful shutdown, and allow use of critical or emergency lights during the outage.
A practical solution for most applications is to provide UPS backup for the lighting control electronics and one LED driver board. In the lighting configuration, such an approach implies that:
- critical/emergency lighting is configured to use LED driver channels on the UPS-backed driver board.
- a separate/isolated power supply be used to power the UPS-backed driver board.
- the UPS system would be the power backup for both the 12 V DC power supply used to power control electronics, and the power supply used to power the subject driver board.
If the subject driver board is loaded to capacity and all lights are operating at 100%, the UPS load would be about 750W. Under most circumstances, this load could be reduced to approximately 100W by dimming or turning lights off thus reducing the load further.
UPS systems are available from a variety of manufacturers. As an example, the SUA1000XL UPS is available from APC. Its 1000VA capacity would easily handle the subject load, bundled with additional battery packs for extended duration. Two such battery packs available from APC are the SUA24XLBP and the rack-mount SMX48RMBP2U.
A runtime graph is available on the APC website that shows runtime vs load condition for variety of UPS & batter pack configurations. For example, data from the graph suggests, for a 100W load the UPS can be designed to operate the lighting system in a power-off condition for up to 50 hours, and at 800W for up to 3.5 hours, depending on battery configuration.